In some regions in China where their traditions during the Chinese New Year are overlooked, there is a norm that during the New Year they must stay late at night and drink “Silver Water”. It is the deep well fresh water that is drank at exactly midnight. It is believed that whoever drinks silver water will gain health for the New Year. People are rushing to the well in the bamboo forest with their buckets and flashlights at the eve of the New Year. With this tradition, clean water is a vital part in their activities. In china, many of the wells are already polluted and contaminated thus they need water purification and filter technologies to gain clean water on their wells or water sources.
Veolia water technologies’ Hydrotech filter system fits within a very compact footprint and was selected as the ideal solution to minimize the installation cost. The filters provide an efficient reduction of organic load to the biological stage without using any chemicals, require little maintenance and offer a high degree of operational flexibility. Collection system first flush conditions were included in the design basis since feed channels to the plant provide a very large buffer storage, allowing for longer periods at increased flow and maintaining a high feed concentration. The Veolia Hydrotech Drum filters were the ideal choice for the client’s challenge, with 20 units of model HDF2010-2F installed to meet the peak loading conditions. The installation requires very limited space, with the filters configured in two main rows that are fed by a common channel in order to optimally use the cavern’s width. The units are automatically taken in or out of operation according to inlet loading in order to optimize the system operation and allow for operational flexibility. Treatment of wastewater at SNJ takes place in stages. First, the wastewater is pretreated by screens followed by grit and sand traps. Next, the Hydrotech Drum filters provide primary solids removal. Wastewater flows from the filters to the biological treatment system to provide BOD and phosphorus removal. Finally, the wastewater is polished by sedimentation. The Hydrotech Drum filters remove particulate organic material ahead of the biological stage, thereby reducing loading and aeration demand. The filtered sludge is thickened along with the biological sludge and sent to the digesters for energy recovery. The Hydrotech filters provide a very efficient TSS removal while maintaining a high throughput. There is no need for chemical addition (coagulant or polymer) prior to the filters in order to reach the targeted TSS removal efficiency. This reduces operating costs and provides an even more space efficient installation. A pilot study was conducted by Veolia water technology prior to the full-scale project installation in order to confirm the removal capability of the Hydrotech filters for this wastewater. The TSS removal efficiency was found to be >45% throughout the pilot trial and averaged greater than 50% for inlet TSS concentrations above 100 mg/l. The results were obtained without any chemical addition prior to the filter system.
We just sent you an email. Please click the link in the email to confirm your subscription!
OKSubscriptions powered by Strikingly